IR Sensors Overcome Silicon Dust Problem
Aug 11 2020 Read 567 Times
A state-of-the-art Energy from Waste (EfW) facility in the North East treats enough residual waste to generate electricity to power 63,000 homes.
At the incinerator, there are four burners. The incinerator burns general household waste that can't be recycled. As a result of burning residual waste, dusty ash escapes into the atmosphere inside the plant. These dusts can contain plastics, silicones and several other possible inhibitors that could be detrimental to the life of a gas detector.
The Problem with Pellistor Sensors
There are 2 detectors on each of the 4 burners that are used to measure hydrocarbons.
Hydrocarbons are installed to measure 0-100% LEL and the risk of explosion within the facility.
When the EfW site was constructed, pellistor sensors were installed to measure hydrocarbons. A pellistor sensor is commonly used to detect combustible gases within the explosive range to warn of rising gas levels.
Once operational, the site recognised that there was a problem with the gas detectors because of low readings during a gas test. The readings were much lower than expected based on previous testing. The operations team made the decision to replace the pellistors with new sensors as a means for fixing the problem. However, after just 3 weeks the new sensors were only reading 13%LEL when using %50LEL gas - a drop of almost 75% in readings from what it should be.
Site realised they were faced with the same problem.
The site turned to a1-cbiss who were invited to conduct a site survey and identify what was going wrong.
The Site Survey
a1-cbiss carried out a thorough site survey to check the site conditions, understand the waste materials, and analyse current gas readings.
The site survey concluded and a1-cbiss believed that the issue was with the pellistor sensor technology, given the potential for silicone particles, fine dust and other potential inhibitors in the sites atmosphere”.
The problem with pellistor technology is that they're prone to poisoning from silicones commonly found in household items.
If partially coated, the sensor response is reduced significantly, however if it is fully coated, the pellistor sensor can no longer burn, and as such cannot detect any combustible gas. Inhibitors on the other hand can desensitise the sensor and shorten its life.
The IR Sensor Solution
a1-cbiss were confident that the problem would be solved by replacing the pellistor sensors with IR sensors. IR sensors can't be poisoned and provide a fast response. The biggest advantage is that IR technology provides fail-safe testing. This means that if the infrared beam was to fail, the user would be notified of this fault on the detection control panel.
The GD10 Series from Oldham is so stable that an ultra fast speed of response can be achieved. The GD10 IR sensors provide unparalleled service life and detector stability, thus saving on maintenance and service costs. This is backed up with the longest combined detector and IR source warranty on the market.
Book a Site Survey to Fix Solve Your Site Issues
Do you like or dislike what you have read? Why not post a comment to tell others / the manufacturer and our Editor what you think. To leave comments please complete the form below. Providing the content is approved, your comment will be on screen in less than 24 hours. Leaving comments on product information and articles can assist with future editorial and article content. Post questions, thoughts or simply whether you like the content.
In This Edition Business News - Space weather monitoring to get major upgrade in new research programme - Monitoring weather conditions on Mars - Environmental researchers from Linnaeus Uni...
View all digital editions
Oct 05 2020 Virtual event
Oct 05 2020 VIRTUAL EVENT
Oct 06 2020 Kuching, Malaysia
Oct 06 2020 St. Petersburg, Russia
Oct 06 2020 Valencia, Spain